Get your comfort on in Addison, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own Addison, TX community.
for Addison, TX
Our Reviews by City
sides pea farm - Addison, TX
Exactly what was promised
Paul - Addison, TX
We hope the third time was the charm, but I am not confident regarding a correct installation.
Carol - Addison, TX
We had an evaluation of the problem on Tuesday, and the soonest they would repair the coils was Saturday. They did the service Saturday, but the drain line was not correctly assembled, and I had to call on Sunday and on of the technicians from Saturday re-assembled the line and corrected the problem. However, Monday I still had a hot house and the AC was running non-stop. I called and was told I would have to pay for after hours service to look at the problem. I indicated that this was a continued problem with their installation and that I wanted to speak with a manager. The technician called back promptly and said he was on his way and there would be no additional charge. The new technician informed me that the freon was low and that possibly the installation on Saturday may not have been correct accounting for another leak. He said to call on Tuesday if the house was not cooling properly. The house was cool this morning, so I am hopeful that the Saturday technicians just did not put enough freon in the system. I am quite worried that I will not know that the problem was solved until I get home today and see the usage on the unit.
Very pleased with timeliness and service/cost
steve - Addison, TX
kevin - Addison, TX
Appreciate the quick response after hours. Tech was thorough and did great work!
chang - Addison, TX
We thank Dale for coming to fix our heater unit. He was courteous and diagnosed the problem very quickly. He explained to me the issues and repaired our motor without issues. We have always used Air Force One because we think it's the best company around. It's the first company we call when we need assistance. Please keep it up. Thanks.
Technician Ricardo performed to diagnostic analysis one conventional gas addicts system the other is a conventional 2 zone system controls both the first and third floor the zone board is becoming defective had to add jumpers just to get it to function for the first floor also both the outdoor compressors when calling for cooling and have been off for a while are starting up hard with settling liquid refrigerant recommend crankcase heaters and/or 3 tonnage bolt on expansion valves.
PREPAID HEAT CHECK. LEFT NEW FITLER (2). Co GOING OUT OF FLUE PILE 8-10 PPM OK. Co I SIDE AIRSTREAM 0PPM OK. CAPACITOR OK. CLEAND OFF FLAME SENSORS. (2). BLOWER WHEEL OK. MOTOR AMPS OK. TD-55-60 OK. HEAT CHECKS OUT WORKING FINE ON TEST DATE.
Worked on 2 frezzer units (404a).... replaced defective thermistat on the ~m#med317b indoor . (Back unit (smallone) front larger unit checked out just fine. Now front unit @3�??Back unit @5�.
Replaced 3 ton r22 outside condenser only, w/ same size unit. New liquid line dryers. Recharged w/ 7lbs r22.
Cooling check 2 units water washed cond coils . Need to be done every 30-60 days due to lent from dryer, cleaned out main drain lines, all electronics checked normal, temp drop 1820
Repaired leak @ coil,replaced liquid line dryer, pressure tested @450psi micron rested @ (vacum pumped)@ 400microns, added 4lbsr22, still need to change 50/5/440 dual run cap,& water wash condensing units every30-60days
Need to replace blower wheel, pulley, blower shaft, blower bearings and the parts that hold the bottom bearings in place. The bottom bearing have worn out so bad it has made it to where it is now rubbing metal to metal.
Performed a4 system cooling check water washed all condensing coils replaced all media filters and water washed all Electric static filters added chlorine tablets into main drain lines to help keep clean also found the one-room system sweating causing insulation to be all wet and drip inside sped up endure fan speed and recommend replacing the 10 inch duct and adding duct wrap
Completed mini split gree system installation on a two car garage conversion
Tech found defective start Kit assist for the compressor was out replace starter kit system started operating just fine no other issues found at this time
Technician found on unit number 5 defective shorted to ground scroll compressor also found contactor and two capacitors starting to get weak that will need to be replaced with compressor will need to replace also fuse at the outdoor fuse box
Ricardo found outdoor contactor ,capacitor and newly installed Start Kit melted altogether including the wires replaced all defective parts and fixed all the wires. Tested the cooling system and now is operating normal
Technician Ricardo found overflow water switch wired only to turn off the outdoor unit causing it to turn off and on off and on and eventually ruined the dual run capacitor outside rewired the overflow switch to turn off the system replaced the outdoor capacitor system operating normal now
Rick returned to find small cracks in the PVC P trap and as soon as the Rick moved the PVC more pieces started to crack and fall apart maybe was still leaking through the small cracks went ahead and replaced PVC P trap and re insulated
Rick found bad dual run capacitor outside stopped up condensing coil that should be water washed every 30 days 20 X 25 X for Honeywell filter stopped up needs to be replaced every 90 to 120 days also found system lo anywhere from 4 - 5 lbs of freon R 22. performed electronic leak check indoor coil is leaking a refrigerant recommend replacing equipment or replacing cooling equipment only or attempt to patch system with Super Seal
Rick found PVC threads not sealing causing water to eventually drip. added sealant and made sure no more water would leak through the PVC threads. No other issues found
Blew out main drain line that was clogged,recommended bleach for preventing drain to clogge
Cooling Check of one lennox system. Filter needs replaced 16x25x1. Coils were clean, checked motors, capacitors and electrical, ok. R22 charge was normal.
Cooling Check of 2 systems. Replaced filters 20x20x1, 16x20x1, 16x25x1. Washed condenser coils, checked motors, capacitors and electrical. Upstairs evaporator coils need to be replaced.
Unclogged stopped up drain line.
Cooling Check of one carrier system. Filter was ok 20x25x1. Checked 410a charge ok. Inspected blower, electrical, drains. Tested capacitors and motors.
He check on new install water washed outside from dryer debris New Rheem Heat Pump ready for winter