Get your comfort on in Allen, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own Allen, TX community.
for Allen, TX
Our Reviews by City
Prompt, professional service
Dale - Allen, TX
green - Allen, TX
On time neat and honest
David - Allen, TX
I switched to AF1 after being ripped off by a previous company on several occasions. AirForce is extremely reliable and honest.
Beth - Allen, TX
The techs (and in fact everyone I've dealt with) are always very courteous and professional. They strive to do a good job and keep their customers happy. And even if things don't work out as we all hoped (our outside unit turned out to be a lemon), they will make sure it is right in the end. That's a business culture others could learn from.
Wow, very honest personnal and super professional......
david - Allen, TX
They are the perfect business to ask for a service.
Heating Check up 2 systems both lenoox furnace are working great.
Prepaid furnace inspection 2 carrier systems both are new and working great..
Replace defective capacitor on main living area system 45+5uf refrigerant levels normal all working fine
Found leak inside evaporator coil will check for replacement asap.
Two systems maintenance tune up freon was added to upstairs system for better cooling both systems are ready for the summer
Cooling check of two systems york 10seer both are working properly.
Technician ricordo perform diagnostic on a gas carrier horizonal right furnace in the attic found the flame sensor faulty and needing to be replaced replaced it tested all other heating components to make sure no other issues were found everything else checked out fine is heating turned on just fine and cycled his thermostat off and on just fine should be ready for any more snow if we get any
Replaced 75 bolt hot surface ignitor on a Lennox system
Preventive check on 1 Lennox system And 2 diagnostic analysis on Lennox furnaces w/ bad combustion motors Systems ready for winter after replacing the 2-7.5mfd caps
Heating Check 1 system
Preventive he check on to Lennox gas fired units everything checks fine ready for winter
Carrier system operating normal
Fixed sticking damper motor
Lennox system check