Get your comfort on in Allen, TX with top quality AC repair, heating and plumbing services from the professionals at Air Force One. We have over 25 years of HVAC & plumber industry experience. We are a family company dedicated to providing you with family treatment.
Read recent reviews below of our five star plumbers and HVAC techs from your own Allen, TX community.
for Allen, TX
Our Reviews by City
Prompt, professional service
Dale - Allen, TX
green - Allen, TX
On time neat and honest
David - Allen, TX
I switched to AF1 after being ripped off by a previous company on several occasions. AirForce is extremely reliable and honest.
Beth - Allen, TX
The techs (and in fact everyone I've dealt with) are always very courteous and professional. They strive to do a good job and keep their customers happy. And even if things don't work out as we all hoped (our outside unit turned out to be a lemon), they will make sure it is right in the end. That's a business culture others could learn from.
Wow, very honest personnal and super professional......
david - Allen, TX
They are the perfect business to ask for a service.
Technician arrived and found the pilot on the right hand side water heater was not lit. Technician demonstrated to the customer how to relight the pilot light and set the water temperature to hot. Both water heaters are currently lit and working as intended.
Gave the customer a quote for replacing the system he will get back to us with his decision
Technicians ran new thermostat wire from entrance of the home to the furnace above the garage. New thermostat was installed at the entrance and programmed. Existing humidifier interface module was bypassed and set to run in cool mode only. New drain pan float switch was installed and tested. System is currently running and working as intended.
Technician arrived and replaced faulty drain pan float switch. Float switch was tested and worked properly. During installation thermostat failed and after replacing battery technician determined thermostat must be replaced. New Honeywell T3 was installed and thermostat is working but wiring not complete and technicians will return on 7/20 to finish up rewiring and ensure system is working properly.
Humidity levels in the house are around 70%. Checked unit and there are no holes in duct work. Fresh air intake works perfectly. Closes when not called for. Static pressure is .02. Temperature differential is 20 degrees. Unit is working perfectly fine. Customer signed up for membership. 2 visits for maintenance (1 in the fall, 1 in the spring), 15% discount on repairs, 5% discount on new system, $69 trip fee regular business hours, $89 trip fee after hours.
Low voltage short on system. Popped fuse. Checked low voltage wiring and determined the float switch was causing the short due to the electrical storm a couple days ago. Disconnected float and tested unit. It is cooling at this time now. Will come back and replace the float switch at a later date.
2.5 Ton Lennox 14 SEER Single Stage Horizontal Attic Install. 10 Year Parts, Labor, and Refrigerant Warranty. Adding 4 Inch Glassfloss Filter Plenum.
Give customer quote customer will get back to us with time and date for install
Unit is frozen will return tomorrow to further diagnose
Technicians descaled two Rheem outdoor tankless units to maintain efficiency and reduce wear and tear. A water mark appeared near the customerâ€™s shower. Technicians attempted to replicate the conditions to make water mark appear but were unable to do so. Customer was informed to call next time the mark appears or if it gets worse.
Filters are in system. Attached are the photos of the filters in the units. Filter access is located in the attic next to the return plenum. Return grills on ceiling do not require filters as the systems have a 4 inch filter in place. One filter per unit is needed. Homeowners have extra filters in the attic.
1 system spring PM. Checked electrical components. Replaced air filter. Coils are clean. No issues or follow ups needed at this time. System is ready for summer weather.
Perform system maintenance talk to the customer about air quality improvements customer declined only recommendation at this time is air care quality improvements and separating the drains that are both tied in upstairs System is performing to manufacturer specifications at this time
Perform system maintenance no recommendations at this time customer was concerned about co2 detector in house co2 detector has 10 year battery life and is still operating will monitor the health of it as time goes on And recommend replacement when that time comes
2 system spring tune up. Checked furnace blower and coil. Checked duct work and drain lines. Replaced filters. Checked electrical components. Checked outdoor condensing unit. Cleaned coil with water. Checked refrigerant pressures. Checked fan and compressors. All electrical components check out. No issues found at this time. Customer paid in full.
system maintenance on all 3 systems talk to the customer about downstairs left unit having a dirty filter customer will proactively change filter in the future to avoid problem persisting other than that no recommendations at this time units were install 7 months ago Please see attached notes and make sure the following filters are on for the future tuneups 20 Ã— 25 Ã—4 x2 16Ã—15 Ã—4 Ã—1
Found leaks inside evaporator coil and condenser Send customer quote
Install new Linux furnace sl28ouh090v6oc
Heating Check up 2 systems both lenoox furnace are working great.
Prepaid furnace inspection 2 carrier systems both are new and working great..
Replace defective capacitor on main living area system 45+5uf refrigerant levels normal all working fine
Found leak inside evaporator coil will check for replacement asap.
Two systems maintenance tune up freon was added to upstairs system for better cooling both systems are ready for the summer
Cooling check of two systems york 10seer both are working properly.
Technician ricordo perform diagnostic on a gas carrier horizonal right furnace in the attic found the flame sensor faulty and needing to be replaced replaced it tested all other heating components to make sure no other issues were found everything else checked out fine is heating turned on just fine and cycled his thermostat off and on just fine should be ready for any more snow if we get any