Get your comfort on in Carrollton, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own Carrollton, TX community.
for Carrollton, TX
Our Reviews by City
Mike - Carrollton, TX
Again brought wrong air filter
Elizabeth - Carrollton, TX
Air Force One arrived on time, completed the project in good time, explained the process, and charged me a fair price. I can’t recommend them enough!
Response from Air Force One Plumbing, Heating & Air:
Thank you for giving us five stars We look forward to helping you out in the future!
Great Company ~ Great Service
manson - Carrollton, TX
Always know that our heat and air are being taken care of by a PRO! Thank you for consistently giving us great service!
rex - Carrollton, TX
timely service, very professional, cost was reasonable, polite service
bian - Carrollton, TX
Very Satisfied Customer
manson - Carrollton, TX
We have been using Air Force One for years because they are honest & reliable. We feel very lucky to have Dale R as the technician they send out. He is always prompt & professional.
sam Cooper - Carrollton, TX
good quick service
duncan - Carrollton, TX
Kevin came out on time and quickly checked all the possibilities of why my AC unit wasn't coming on. It turned out to be just a loose wire in my thermostat, so he fixed that. He also gave me some advice on replacing my old condenser and coil, which is on my list of improvements to my home.
manson - Carrollton, TX
This company provides a great service & they are honest!!
Cody Pierce - Carrollton, TX
Technician came out on Thursday, November 13th. He informed us that we needed a new furnace and he would have us an estimate either later that day or the next day. When I had not heard anything by Tuesday morning I called the office and they said they would see what happened and get back to me shortly. I still have not heard anything so I assume Air Force One is not interested in my business. I will have to proceed with another company.
Kevin answered all my questions and provided excellent service.
Bob - Carrollton, TX
Indoor unit inspected air filter is actually a 14x25x1 told customer wouldnreturn at end of day with new filter. Outside unit inspected only fault found was debris in the outside coil unit was rinsed down and issue resolved.
2.5 Ton American Standard Single Stage Attic System. Quote includes equipment installation, 10 year parts labor and refrigerant warranty, moving refrigerant lines into the attic, and modifying duct to attach to current chase system. Additional duct modification would be extra
Inside unit inspected for any electrical or mechanical faults. None were found both air filters were replaced. Outside unit checked for electrical and mechanical faults.none were found, but refrigerant was half empty no leak could be detected. Customer was made aware of the problem and recommended replacement due to lack of parts for r-22 systms. She is waiting to hear from Josh with a quote
Inside up and down stairs unit inspected for electrical and mechanical abnormalities and faults None were found everything is working and cooling as expected. Both outdoor units were inspected and coils washed to remove any dirt and debris. Drain lines were inspected and a quote will be emailed for rerouting them to drain from the 1st story
Completed system maintenance found outside condenser low on refrigerant and drain line having problems talking to the customer about recommended repairs
Damper for the upstairs bedroom was closed. We closed it in the winter because it was getting too hot in the room. Customer will close and open the damper as the weather changes. Open for summer. Partially closed for winter. No other issues found at this time.
System was low on refrigerant. 5 pounds low. Added r-22 and superseal with dye. Unit is working properly at this time now. 20 degree temperature differential. No other issues found at this time. System is working as designed.
Move duct that is blowing on bed to the doorway. Fix non working damper. Sheet rock repairs not included.
Will send quote to move duct and check if damper for downstairs bathroom is working.
1 system spring PM. Checked temperature differential. Checked blower motor amps. Replaced air filter. Duct work and drain line are good. Checked condensing unit. Checked amps of compressor and fan motors. Checked capacitor. Cleaned coil with water. No issues found at this time. System is ready for summer weather.
Installed 18â€ return duct. Moved supply duct from bedroom to return. Installed 2 ecobee thermostats + sensors. Customer signed water damage waiver since return plenum is non-insulated and could cause condensation issues in the future. Units are tested and working properly at this time.
Merit Series, Upflow/Horizontal Gas Furnace, 80% AFUE, 88,000 Btuh, Power Saver Constant Torque, 1 Stage, 3-5 Ton, ML180UH090E60C
Returning on Monday to replace Unit
Clean flame sensor system is working as usual
Sending quotes for ecobee thermostats and sensors and one return duct.
Reset limit switch on a york furnace and installed a honeywell thermostat
Maintenance check up two systems prepaid both systems are working great..
Replaced gas valve on trane furnace . checked furnace all working properly.
Heating Check of one trane system. Replaced filter 16x25x1. Tested for carbon monoxide, tested safeties ok. Checked motor amps, capacitor and electrical. Checked thermostat operation, working. System is operating safely and efficiently.
Blew out TNstopped up drain with compressed air.
Found system low on r22 frwon, added 3lbs of r22 and super seal to downstairs system
Heating tune up of one rheem furnace. Filter was clean, 16x25x4. Cleaned flame sensor, tested safeties, cleaned the flame sensor. Found no carbon monoxide leaks and the furnace was burning properly.
Call back from after hours service call found the low voltage fuse blown. low voltage wire going outside shorting out fuse will need to be replaced. Also found week outdoor capacitor and 1 l_b_s low of R22 freon customer will clean condenser coils outside every filter change ....tech will return saturday to run new thermostat wire to the outside
Found capacitor on carrier condenser readin 0 mfd and leaking. Also needs fan blade replaced, has a crack in it.