Get your comfort on in Carrollton, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own Carrollton, TX community.
for Carrollton, TX
Our Reviews by City
Elizabeth - Carrollton, TX
Air Force One arrived on time, completed the project in good time, explained the process, and charged me a fair price. I can’t recommend them enough!
Response from Air Force One Plumbing, Heating & Air:
Thank you for giving us five stars We look forward to helping you out in the future!
Great Company ~ Great Service
manson - Carrollton, TX
Always know that our heat and air are being taken care of by a PRO! Thank you for consistently giving us great service!
rex - Carrollton, TX
timely service, very professional, cost was reasonable, polite service
bian - Carrollton, TX
Very Satisfied Customer
manson - Carrollton, TX
We have been using Air Force One for years because they are honest & reliable. We feel very lucky to have Dale R as the technician they send out. He is always prompt & professional.
sam Cooper - Carrollton, TX
good quick service
duncan - Carrollton, TX
Kevin came out on time and quickly checked all the possibilities of why my AC unit wasn't coming on. It turned out to be just a loose wire in my thermostat, so he fixed that. He also gave me some advice on replacing my old condenser and coil, which is on my list of improvements to my home.
manson - Carrollton, TX
This company provides a great service & they are honest!!
Cody Pierce - Carrollton, TX
Technician came out on Thursday, November 13th. He informed us that we needed a new furnace and he would have us an estimate either later that day or the next day. When I had not heard anything by Tuesday morning I called the office and they said they would see what happened and get back to me shortly. I still have not heard anything so I assume Air Force One is not interested in my business. I will have to proceed with another company.
Kevin answered all my questions and provided excellent service.
Bob - Carrollton, TX
Merit Series, Upflow/Horizontal Gas Furnace, 80% AFUE, 88,000 Btuh, Power Saver Constant Torque, 1 Stage, 3-5 Ton, ML180UH090E60C
Returning on Monday to replace Unit
Clean flame sensor system is working as usual
Sending quotes for ecobee thermostats and sensors and one return duct.
Reset limit switch on a york furnace and installed a honeywell thermostat
Maintenance check up two systems prepaid both systems are working great..
Replaced gas valve on trane furnace . checked furnace all working properly.
Heating Check of one trane system. Replaced filter 16x25x1. Tested for carbon monoxide, tested safeties ok. Checked motor amps, capacitor and electrical. Checked thermostat operation, working. System is operating safely and efficiently.
Blew out TNstopped up drain with compressed air.
Found system low on r22 frwon, added 3lbs of r22 and super seal to downstairs system
Heating tune up of one rheem furnace. Filter was clean, 16x25x4. Cleaned flame sensor, tested safeties, cleaned the flame sensor. Found no carbon monoxide leaks and the furnace was burning properly.
Call back from after hours service call found the low voltage fuse blown. low voltage wire going outside shorting out fuse will need to be replaced. Also found week outdoor capacitor and 1 l_b_s low of R22 freon customer will clean condenser coils outside every filter change ....tech will return saturday to run new thermostat wire to the outside
Found capacitor on carrier condenser readin 0 mfd and leaking. Also needs fan blade replaced, has a crack in it.
Found outside condenser clogged with Cottonwood water washed coils checked refrigerant levels normal all working fine
Maintenance check up two systems replace filters drain lines clear motor amps ok water washed coils refrigerant levels ok
Found system low on r22 refrigerant three pounds was added recommended replacement will address in a later date
Replaced evaporator motor on upstairs furnace all working fine
Technician Ricardo found defective thermostat reading 10 degrees when it's 80 degrees switched out programmable thermostat Emerson programmed and tested cooling refrigerant level checked normal temperature drop at system 18 degrees filters were still ok drain lines were clear no other issues were found at that time
Technician Ricardo perform a preventive cooling check sound system low 1lbs of R 22 leak locked threads at shutoff valve caps where the leak was all other electronic parts inside and out checked normal water wash condenser coil was very stopped up swapped out old filter 16X25X4" cleared and cleaned main drain line temperature drop across air conditioning system inside 20 degrees no other issues found at this time system is ready for the summer
Technician Ricardo and Subcrew replaced under 10 year warranty the dream compressor and the leaking evaporator coil pressure tested system at 450 psi and then a negative pressure test at 500 microns recharged system temperature drop at system 20 degrees ready for a hot summer
Technician Ricardo Moreno found 2011 410a refrigerant system has a compressor knocking or sounding bad and most likely is due to the indoor evaporator coil leaking out most of its refrigerant both are covered under our 10 year parts labor and free on warranty good thing the customer had that warranty for now technician has left the outside unit inoperable to not cause any more issues or damage that are unnecessary office will schedule parts replacement
Maintenance check up carrier system13 seer recommended items to make system better
Maintenance check up flow trane system is in great working condition