Get your comfort on in Frisco, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own Frisco, TX community.
for Frisco, TX
Our Reviews by City
mr - Frisco, TX
he was great will use again
Holton - Frisco, TX
Response from Air Force One Plumbing, Heating & Air:
Glad to hear it. Thanks for the review
Very satisfied with the service.
jim - Frisco, TX
I just renewed service for another year. Service and price must be good for me to keep coming back.
great job as always!
Tom - Frisco, TX
We were in need of a check up and gave Air Force One a call. They were here quick and Kevin did a great job as always.
JIM - Frisco, TX
Professional service. Prompt response when called to handle a breakdown.Cost competitive.
Consistent and Professional
DANIEL - Frisco, TX
Great company, honest, timely, professional, friendly. Just few words for a company with a long history of quality service.
Found high voltage wire nut exploded in electrical cabinet
system maintenance no gas leaks
Replaced 10mfd capacitor on the downstairs carrier furnace
Technician Ricardo performed diagnostic analysis on the downstairs gas Amana heating system found in the attic second floor tested all the heating and electrical components only found the flame sensor putting out a to millivolt reading replaced and now receiving a 12 Miller both reading and system is up and operating correctly
Blew out drain on downstairs and washed coils on upstairs
Checked conderser for any problems to stage rheem system no problems for detected.all working fine.
Replaced swollen capacitor on york conderser 40+5uf all checks out working fine
Charged 2 stage trane system with 410a freon
Replaced warranty rheem condenser fan motor
Found conderser fan motor locked up will return with warranty motor for replacement
Technician Ricardo diagnosed upstairs system found evaporator coil leaking out three to four pounds of refrigerant also found two week capacitors one for the Flor one for the outdoor unit the 20 X 25 x1 filter was dirty needed to be replaced and outdoor condenser coils need to be water washed every 30 to 60 days recommend replacing equipment due to age and r22 equipment/ refrigerant becoming more and more expensive especially if you plan on staying in the house for the next 10 years
Trane cooling systems 2 both are being well kept
Found dirty filter and rewired furnace for gas heat
Technician Ricardo technician Dale worked on a gree PTAC self-contained system heat pump for the garage issues with the compressor a restriction in the metering device in a leak in the coil condenser coil to be exact may be under warranty will check with manufacture
Replaced capacitor on upstairs system