Get your comfort on in Frisco, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own Frisco, TX community.
for Frisco, TX
Our Reviews by City
Andy - Frisco, TX
Great job as always. Very professional and thorough. It’s why I continue to use AFO for these past 10+ Years.
mr - Frisco, TX
he was great will use again
Holton - Frisco, TX
Response from Air Force One Plumbing, Heating & Air:
Glad to hear it. Thanks for the review
Very satisfied with the service.
jim - Frisco, TX
I just renewed service for another year. Service and price must be good for me to keep coming back.
great job as always!
Tom - Frisco, TX
We were in need of a check up and gave Air Force One a call. They were here quick and Kevin did a great job as always.
JIM - Frisco, TX
Professional service. Prompt response when called to handle a breakdown.Cost competitive.
Consistent and Professional
DANIEL - Frisco, TX
Great company, honest, timely, professional, friendly. Just few words for a company with a long history of quality service.
Found unit Clog
5 Ton up to 16 SEER Condenser and Coil
Found outside condenser tripping breaker on the inside recommended condenser evaporator coil replacement customer agrees will be returning later this week to install both
Sending the customer quote for replacement as well as repair
Capped a froze water line in the garage that was leaking due to the hard freeze. Will return to repair at a later date.
Perform system maintenance insurance system is working within manufacturer specifications talk to the customer about the downstairs system having issues With outside condenser coil disintegrating
Replaced segment of 1/2â€ copper line which was removed and capped due to leak. New pex line was installed and tested. No leak present and all fixtures are working.
16 SEER Two Stage American Standard Gas Furnace
Returning on Wednesday at 8 to install new furnace
Flipped Breaker will revisit on Friday to further diagnose
1 system spring PM. Checked blower motor amps. Checked temperature differential. Inspected coil and duct work. Checked condensing unit. Coils are clean. No issues found at this time. System is ready for summer weather.
Ensure that the systems is Performing to manufacturer specifications No recommended repairs at this time will keep an eye on older unit and see how summer effect it
Found high voltage wire nut exploded in electrical cabinet
system maintenance no gas leaks
Replaced 10mfd capacitor on the downstairs carrier furnace
Technician Ricardo performed diagnostic analysis on the downstairs gas Amana heating system found in the attic second floor tested all the heating and electrical components only found the flame sensor putting out a to millivolt reading replaced and now receiving a 12 Miller both reading and system is up and operating correctly
Blew out drain on downstairs and washed coils on upstairs
Checked conderser for any problems to stage rheem system no problems for detected.all working fine.
Replaced swollen capacitor on york conderser 40+5uf all checks out working fine
Charged 2 stage trane system with 410a freon
Replaced warranty rheem condenser fan motor
Found conderser fan motor locked up will return with warranty motor for replacement
Technician Ricardo diagnosed upstairs system found evaporator coil leaking out three to four pounds of refrigerant also found two week capacitors one for the Flor one for the outdoor unit the 20 X 25 x1 filter was dirty needed to be replaced and outdoor condenser coils need to be water washed every 30 to 60 days recommend replacing equipment due to age and r22 equipment/ refrigerant becoming more and more expensive especially if you plan on staying in the house for the next 10 years