Get your comfort on in Irving, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own Irving, TX community.
for Irving, TX
Our Reviews by City
Thorough, friendly and professional. Thanks!
jill - Irving, TX
Suresh - Irving, TX
Was very professional and knowldgeable
Condenser fan motor (CFM) had loose bearings. Replaced CFM with aftermarket motor. System is cooling properly at this time now. No other issues found.
System was low 2 pounds of r22. Added refrigerant and system is cooling properly at this time now. No other issues found. Returned system to operating settings.
Perform system maintenance talk to the customer about recommended upgrades Remy Halo customer declined at this time system is performing to manufacturer specifications
2 system spring PM. Checked blower motor amps. Checked temperature differential. Inspected coil and air flow. Replaced filters. Checked condensing unit. Checked fan and compressor amps. Coils are clean. No issues found at this time. System is working as designed.
Service contract furnace inspection rheem system, Co inside airstream 0ppm, Co going out flue normal, filter was ok,inducer motor amps :ok System working properly.
Cooling check of 2 systems found both indoor and outdoor capacitors low needing to be replaced main drain line clogged needed to be cleaned both outdoor units needed to be washed and main system needed about 1 lbs of r22 otherwise systems or cooling just fine and you still have available 2 heat checks available