Get your comfort on in McKinney, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own McKinney, TX community.
for McKinney, TX
Our Reviews by City
cameron - McKinney, TX
crain - McKinney, TX
Best HVAC Tech Ever!
Rose - McKinney, TX
Rick came out and had my compressor back up and running quickly. He is always thorough and diagnoses the problem easily. He is polite and friendly and cleans up after himself. He is a valuable asset to any HVAC company. Thanks Rick for an awesome job!
Michael - McKinney, TX
Ya'll are awesome for coming so fast on a Saturday and Rick was great. Thank you!
Good, Fast and Friendly Service
Rose - McKinney, TX
I've used Air Force One Air Conditioning several times now and every time I've used them they've done a good job. Rick came out and diagnosed my problems quickly and had it repaired quickly. He didn't mind my questions and happily explained what I wanted to know. They have good customer service and their techs are knowledgeable. Pricing is a bit high but that's the case no matter who you call out for AC work.
Bruce - McKinney, TX
Dale was very courteous and professional. He thoroughly checked my heating systems to make sure they were working properly.
Added 3 lbs of r22 to lennox system
Found defective blower wheel on furnace will need to be replaced I'll show emergency drain pans rested needs to be replaced will send out bid on replacement on 5 ton system
Cooling Check of 2 carrier systems. Replaced 3 capacitors, added celing saver to one system, replaced one voltage controller and added 2 compressor savers. Water waahed condenser coils, ch ecked freon levels.
Technician Ricardo was out in McKinney working on a dream conventional gas heat air conditioning system found miss wired capacitor sticking contactor dirty evap coil and blower and a week blower capacitor recommending using pleated filters once wiring and contactor was replaced refrigerant levels checked normal no other issues were found system is ready for
Technician Ricardo found outdoor capacitor bad causing compressor not to turn on had to also add a Start Kit with new capacitor compressor seems to be getting weaker but now after replacing defective part and adding the Start Assist system is operating normal now refrigerant levels checked out normal temperature drop across the indoor air handler 18 degrees other than that no other issues were found ready for a hot summer
Technician ricardo arrived at a call back Saturday found outside condenser motor locked bearings going out very hard to turn system tripped on high pressure safety switch will need to find out if system is under warranty Monday if not we'll need to charge or the motor and evap coil that is leaking other than that system is operating normal now we thank you for your business
Technician Rick diagnosed outside unit not coming on due to 1 pole contactor defective causing only 115 volts out of 240 through replaced defective contactor check refrigerant charge recommended washing outdoor unit every month or two other than that refrigerant level checked fine no other issues at this time awesome people thank you for the eggs that's pretty cool we thank you for your business your system should be ready for a hot summer
Technician ricardo found debris of tape causing water from coil to drip and roll around on tape to the air handler casing... Removed all debris cleaned all water in emergency pan and double checked all drains once tape was cleared away water was draining correctly into main waste water pan did also find a small supply outlet hole from old tape coming off went ahead and resealed all air leaks there at supply plenum system ready for a hot summer
Technician Ricardo perform diagnostic on a Goodman air handler found in the attic horizontal right heat strips stuck on replaced both heating sequencers tested motor heat strips and amps all check normal after defective parts replaced system ready for winter
Replaced warranty thermostat
Preventive heat check on two carrier gas furnaces No issues found at this time Systems ready for winter
Heating Check 2 systems
replaced downstairs rheem condenser capacitor
rheem condenser water washed