Expert Heating, Air Conditioning & Plumbing Services in Mesquite, Texas
Both your HVAC systems and your plumbing are very important parts of your home. When they break down or they’re no longer able to function as well as they should, your comfort and safety can be put at risk, as the quality of your air and water can be compromised if your systems aren’t filtering out contaminants.
If you’re having plumbing or HVAC problems, it is vital that a trained professional diagnose the issue and solve it using the best method for the situation. The team of experts we have at Air Force One Plumbing, Heating & Air have all been trained to know how to spot problems and thoroughly fix them so they won’t give you any more trouble.
When it comes to speedy services and effective work, you can count on Air Force One to exceed all of your expectations. Our friendly staff and our experience of over 25 years make us the perfect team for any and all of your HVAC and plumbing problems. We offer installation, maintenance and repair services, so no matter what you need, we’ve got you covered.
Rely on Air Force One for:
- Sewer Line Clearing
- Water Heater Installation
- Shower & Tub Repair
- Heating Service
- Air Conditioning Service
- HVAC Maintenance
For more details on the services we offer in the Mesquite area, give us a call at 469-476-4846 and we’ll be happy to answer any questions you may have.
Why Choose Us:
- 24/7 emergency HVAC services available.
- We get the job done right the first time.
- We are a family owned business.
- We have over 25 years’ experience.
for Mesquite, TX
Our Reviews by City
Great Service People!
Tim - Mesquite, TX
great service, techs are well trained
Chuck - Mesquite, TX
Mike - Mesquite, TX
Rick came out to install new part and checked out system and had it running to perfection. On time and wore covers on boots, very important to my wife.
Rick the service tech did a great job however the person doing scheduling dropped the ball.
don - Mesquite, TX
Rick did a great job, however the lady that makes appointments forgot to schedule ours. We called for an appointment on Monday 11/2 to do our fall check and she told us she would schedule us for 11/12 from 1:00 to 3:00pm. When no one showed up by 3:00 on Thursday we called to see when the tech would arrive. The lady told us she forgot to log the appointment. I advised her that I took off work so I could be here so she needed to get someone out today. She said she was sorry and would get a tech out as soon as possible. We have been a good customer for over approx. 20 years and we have never encountered this. It also worried us that the lady initially told us she couldn't find our account in your files.
Rick is always great in what he does.
Liz Polanco - Mesquite, TX
Very friendly, considerate, hard-working and very willing to answer any questions. I am so glad that he takes care of my air conditioning set-up so well. You are lucky to have such a great employee!!!
don - Mesquite, TX
Kevin did an excellent job.
Friendly service, great troubleshooting
mb - Mesquite, TX
Rick was on time, very friendly, and answered all our questions. He performed a very thorough troubleshooting inspection, and recommended a solution. Our a/c is running great ever since. We have used AF1 in the past and were not disappointed this time in the service. Wish freon was cheaper, but I think it is what all the companies charge. But we did get to use a coupon on the service fee which was appreciated! 🙂
very thorough inspection
michael - Mesquite, TX
thorough diagnosis and quick resolution of problems. technician was clean, explained problems, offered solutions. wish I would have received a receipt for my records but did not.
Expedited service call handled with the most sense of urgency!!
Cintas Corp. - Mesquite, TX
Great tech,great knowledge of job, great price
sam - Mesquite, TX
I have also been to the parts shop and I believe that the shop employees have just as much knowledge of the trade and are just as courteous and helpful.
don - Mesquite, TX
the best and i have tried others
faith - Mesquite, TX
will NEVER use anyone else as long as you are around!
barringer - Mesquite, TX
Very courteous and was done quickly.
On time, fast and easy. Can't do better than that.
Woody - Mesquite, TX
Professional, knowledgable, polite...Great service
williams - Mesquite, TX
There were a few minutes of down time while waiting on warranty information, I asked various questions and all were answered with no hesitation. Tech was confident and efficient. There were no surprise expenses on final bill. Pleased to get attic furnace back up and running without any issues. Thank you Air Force One.
always great customer service
Chuck - Mesquite, TX
All teaks are very knowledgeable.
Best service hands down!
DEWAYNE - Mesquite, TX
Very helpful, they will get you out of a jam and help you diagnose your problem, even if you are a DIY type. Service calls are awesome and they don’t try to upsell you on a bunch of upgrades. My problem was complex and the service tech tracked down the problem fast.
Don - Mesquite, TX
Quick and professional service
1 system spring PM. Checked blower motor amps and capacitor. Checked temperature differential. Inspected evaporator and condenser coils. They are clean. Replaced air filter. Checked condensing unit motor amps and capacitors. No issues found at this time. System is working as designed. Customer signed up for 2 year membership special. Has 3 visits remaining.
Perform system maintenance recommendation is air quality improvement recommend hole house ionisation to make the filters last longer Only other thing of note is outside capacitor is showing signs of adverse wearing will monitor to see if degradation occurs
Customer wanted to get a price list of various services and will decide on any proactive plumbing services.
1 system spring PM. Checked blower motor amps. Checked temperature differential. Checked drain lines. Left new filter with customer. Checked condensing unit. Cleaned coil with water. Checked compressor and fan motor amps. Checked refrigerant pressures. No issues found at this time. System is working as designed. Sent customer quote for ecobee thermostat with extra pack of sensors.
Found bad capacitor replace System is working properly at this time
Ensure system was working to manufacturer specifications
Found bad heat kit relays switches transformer
Found system checking out to manufacturer specifications talk to the customer about replacing the thermostat as it is the most likely source of problems Customer agrees and will keep an eye on it
Found no faults with the system
Technician Ricardo perform a warranty mr. slim indoor blower wheel replacement reset the thermostat control reprogram the time and set back to heating at 80� customer can go ahead and set who would ever comfort you prefer no other issues found system is ready for a cold winter and hot summer
Technician Ricardo and Aaron performed diagnostic analysis on a carrier horizontal attic application found the flame sensor not providing enough AVE signal to the control board making it lockout on no flame sensed once the flame sensor was replaced the correct amount of millivolts was received and no other issues hound on the heating system
Technician Ricardo returned to replace outside air and defrost sensor on the Rheem 410 A heat pump system once both sensors were replaced double check free on levels to manufacture specs systems running correctly on both heating and cooling no other issues found system ready for a cold winter
Preventive heat check performed on a Rheem gas attic furnace carbon monoxide levels leaving the system check normal no carbon monoxide levels found inside the home filter still clean but left one extra one for next month temperature rise at 60 degrees no other issues found all safeties working correctly Systems ready for a cold winter thank you for your business from Air Force One in your tech Ricardo
Service contract 1-Year furnace inspection, replaced filter 14X25x2, Co inside airstream 0ppm, Co going out flue pipe 34ppm , motor amps ok, pressure switch port clear, safetys switches tested ok, system working properly
Heating Check of one rheem system. The filter was clean, 16x25x4. Carbon monoxide levels out of the flue were within safe operation, with no leaks in the airstream. All safeties were operating normally. Sealed up ceiling in the closet where equipment is located.
Heat check on horizontal left system found in attic co levels to outside & inside normal, temp rise60�. Would lile bid to replace 13yr old equipment. Keep fresh air kit just need to check when to replace main filter. 4ton system r22 to 410a
Tech found 24v wiring loosing outside replaced wirenuts due to rust built up & broken inside tested over & over couldnt get it to do it again. Working now. Wanting *& waiting for quote
Technician rico found downstairs main system downstairs blower variable speed module and motor needed to be replaced . Tested cooling aftr replacing part. In need of a full cooling check need to return
Loose low voltage wire going to the outside causing system to stay off
Rheem system was frozen, defrosted and found ow on r22 refrigerant. Added 3lbs or r22.
Technician Ricardo performed diagnostic found system low 3 pounds of r22 performed also an electronic leak detection did not pick up anything inside or outside maybe that small of a leak recharged checked everything else no other issues found at this time system should be up to par now
Technician Ricardo and Antonio replaced defective 410a upflow air handler coil replaced liquid line dryer and recharged had to add 2 lbs of refrigerant system not cooling as a 16 degree differential
Notes added by tech Rick on 7/16/2015 5:05:50 PM REME heat pump system lo on 410a refrigerant both liquid and suction line shut off valves leaking very bad added Lee clock but will not be a permanent fix will need a quote to recover all refrigerant replace outside by Flo liquid line dryer and replace leaking service valves
Cooling check 1 system split r22 attic access hallway, furnace horizontal left. 20x25x1 filter still clean. Compressor amp normal, fan motor amps normal, blower amps normal. Blower capacitor 10mfd. Blowers & coils little dirty but still clean enough to work. Condensing unit still clean need to wash every 30-60 days. Same with 1" filter should be changed every 30-60days. Temp drop 20��48�~68��. Ready for summer
Replaced evaporator coil system under warranty 3ton all working fine.