Get your comfort on in Rockwall, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own Rockwall, TX community.
for Rockwall, TX
Our Reviews by City
Came same day I called, came early and fixed air conditioner .
kathy - Rockwall, TX
Always Great Service
wwndy - Rockwall, TX
Have used their service for three years and it's always easy to do, the service guys are polite and know what they're doing.
chip - Rockwall, TX
Dale did a great job!
Great service & Second Opinion
Jennifer G - Rockwall, TX
I needed help with a problem that I had my other AC guy out for 3 times. I called Air Force One because I use them at home to see if they would do commercial work. The did and they were able to have a technician out the same day!! Not only was Kevin quick and friendly, he found the problem and got me a quote to fix it...all on the same day.
lori - Rockwall, TX
Perform system maintenance found outside condenser capacitor going out expect as well as leaky ducks upstairs and high amps on upstairs system due to age Talk to the customer about recommended repairs customer declines at this time no further recommendations other than aforementioned
1 system spring PM. Checked blower motor amps and capacitor. Checked temperature differential. Inspected drain line. Replaced air filter. Checked condensing unit. Coils are clean. Checked fan and compressor amps. No issues found at this time. System is ready for summer weather.
Replaced control board for furnace. Tested system and it is blowing hot air now. No other issues found at this time. Customer signed up for presidential membership.
Need to return to replace circuit board. ICM282A. Also bring a 24X24X1 filter.
Quarterly Preventative Maintenance on 12 units
Up to 16 SEER 4 Ton Furnace with ECM Blower Motor
Diagnosed bad motherboard customer will reconvene with us on Monday to decide whether or not it is time for a new furnace or repair
High voltage wire going to carrier air handler was to small of wire for the amount of heating strips and burnt up. Cut back to bad wire and disconnected one heat strip tp allow system to operate safely.
Heating Check up 2 systems lennox furnace both systems are working great!!!
Replaced condenser fan motor and capacitor on rooftop carrier package unit
Replaced worn out contactor 1 pole and 5uf capacitor on upstairs condenser all working fine after fix..
TECHNICIAN RICK FOUND THAT THE SYSTEM HAS A FREON LEAK AT THE ON THE SUCTION LINE NEAR THE COMPRESSOR AND A CLOGGED THERMAL EXPANSION VALVE ON THE INSIDE COILS. SYSTEM USES THE OLD 410a FREON AND IT HAS ALL LEAKED OUT. REPAIR: - SYSTEM PUMP DOWN - REPAIR LEAK ON REFRIGERANT SUCTION LINE - ADD FILTER DRIER, AS NEEDED - CLEAN OUT INSIDE THERMAL EXPANSION VALVE - LEAK CHECK - CHARGE WITH 410aFREON - TEST SYSTEM
Tech found system had been turning off on high head pressure outside, system needed to be water washed. Indoor filter still clean. Drain line still clean. Just need to water wash condensing unit outside every 30-90days. Also recommend to add stones around unit to help keep clean.
Rooftop condensing unit needs start kit replaced. Customer will change out him self
DIAGNOSTIC ANALYSIS -1 RESIDENTIAL SYSTEM. Found outside dual run cap bad, replaced 25/10/440. Need to water wash condensing unot every 30 - 60 days. Cleaned indoor evap coil all stopped up. Also need to add ptrap for airhandler.
Installed tstat clear cover lock box on one of the lobby thermostats
Replaced half horsepower 240 volt 1075 rpm blower motor on rooftop gas package system unit number 19 Suite number 207 old blower motor running slow causing slugging to compressor and not pulling all the heat from the air
Maintenance check 2system replaced capacitor recommended some parts all working fine
Found trane system low on r22. Added 3lbs r22. Fan motor bearings going out, customer to replace motor.
Maintenance on one lennox system. Filter was clean, inspected drains, checked motors, capacitors and electrical. Blower motor capacitor was low, declined replaxement, and 1.5 pole contactor waa worn but working, declined replacement. Washed condenser coils, checked r22 charge ok.
Cooling Check of one system. Replaced filter 20x25x4,washed condenser coils, checked motors, capacitors and electrical. Replaced thermostat with honeywell pro 6000. Inspected blower, drains. Checked r22 charge ok.
Cooling Check of one lennox system. Replaced 7.5 mfd capacitor, added pan coat to emergency drain pan. Checked r22 charge ok. Checked temperature drop 20 degrees normal, washed condenser coils, checked motors, capacitors and electrical.
Blow out main drain line with nitrogen on master bedroom system
Technician Ricardo Moreno called out to an after hours service call found burnt common wire for the dual run capacitor on the outdoor unit rewired wire tested amperage refrigerant levels and filters everything else checked out normal no other issues have been found may have been a loose connection
Found drain stopped up on one system and no problems with second system.