Get your comfort on in Rockwall, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own Rockwall, TX community.
for Rockwall, TX
Our Reviews by City
Nicholas - Rockwall, TX
Came same day I called, came early and fixed air conditioner .
kathy - Rockwall, TX
Always Great Service
wwndy - Rockwall, TX
Have used their service for three years and it's always easy to do, the service guys are polite and know what they're doing.
chip - Rockwall, TX
Dale did a great job!
Great service & Second Opinion
Jennifer G - Rockwall, TX
I needed help with a problem that I had my other AC guy out for 3 times. I called Air Force One because I use them at home to see if they would do commercial work. The did and they were able to have a technician out the same day!! Not only was Kevin quick and friendly, he found the problem and got me a quote to fix it...all on the same day.
lori - Rockwall, TX
Capacitor completely dead. Replaced with new one unit hasa 17Â° f split.
Inside units running as designed upstairs outdoor unit running to standard. Down stairs outside unit had a blown capacitor which in turn caused the down stairs unit not too cool. Capacitor was replaced and unit returned to normal function
System inspected. Checked the upstairs air handler, checked blower amperage, blew out the drain line that was clogged and is now flowing freely. Checked outside unit disconnect for function, and measured the amperage of the fan and compressor. Checked the dual capacitor for any fault and function works as designed. Air filter was replaced and unit given another once over. Whole system is functioning as intended and to standard.
System was overcharged. Recovered 1 1/2 pounds. It is working properly at this time.
Evaporator is leaking on the TXV capillaries. Will call gemaire tomorrow and see if they have evaporator in stock.
Put in leak sealant system is working to manufacturer specification
Breaker needs to be checked out by electrician. It is hot to the touch and smells Smokey. Customer signed up for 1 year membership.
Perform system maintenance found bad cap on downstairs as well recommended replacing as well as continual maintenance vet
Perform system maintenance found outside condenser capacitor going out expect as well as leaky ducks upstairs and high amps on upstairs system due to age Talk to the customer about recommended repairs customer declines at this time no further recommendations other than aforementioned
1 system spring PM. Checked blower motor amps and capacitor. Checked temperature differential. Inspected drain line. Replaced air filter. Checked condensing unit. Coils are clean. Checked fan and compressor amps. No issues found at this time. System is ready for summer weather.
Replaced control board for furnace. Tested system and it is blowing hot air now. No other issues found at this time. Customer signed up for presidential membership.
Need to return to replace circuit board. ICM282A. Also bring a 24X24X1 filter.
Quarterly Preventative Maintenance on 12 units
Up to 16 SEER 4 Ton Furnace with ECM Blower Motor
Diagnosed bad motherboard customer will reconvene with us on Monday to decide whether or not it is time for a new furnace or repair
High voltage wire going to carrier air handler was to small of wire for the amount of heating strips and burnt up. Cut back to bad wire and disconnected one heat strip tp allow system to operate safely.
Heating Check up 2 systems lennox furnace both systems are working great!!!
Replaced condenser fan motor and capacitor on rooftop carrier package unit
Replaced worn out contactor 1 pole and 5uf capacitor on upstairs condenser all working fine after fix..
TECHNICIAN RICK FOUND THAT THE SYSTEM HAS A FREON LEAK AT THE ON THE SUCTION LINE NEAR THE COMPRESSOR AND A CLOGGED THERMAL EXPANSION VALVE ON THE INSIDE COILS. SYSTEM USES THE OLD 410a FREON AND IT HAS ALL LEAKED OUT. REPAIR: - SYSTEM PUMP DOWN - REPAIR LEAK ON REFRIGERANT SUCTION LINE - ADD FILTER DRIER, AS NEEDED - CLEAN OUT INSIDE THERMAL EXPANSION VALVE - LEAK CHECK - CHARGE WITH 410aFREON - TEST SYSTEM
Tech found system had been turning off on high head pressure outside, system needed to be water washed. Indoor filter still clean. Drain line still clean. Just need to water wash condensing unit outside every 30-90days. Also recommend to add stones around unit to help keep clean.
Rooftop condensing unit needs start kit replaced. Customer will change out him self
DIAGNOSTIC ANALYSIS -1 RESIDENTIAL SYSTEM. Found outside dual run cap bad, replaced 25/10/440. Need to water wash condensing unot every 30 - 60 days. Cleaned indoor evap coil all stopped up. Also need to add ptrap for airhandler.
Installed tstat clear cover lock box on one of the lobby thermostats
Replaced half horsepower 240 volt 1075 rpm blower motor on rooftop gas package system unit number 19 Suite number 207 old blower motor running slow causing slugging to compressor and not pulling all the heat from the air