Exceptional Plumbing, Heating & AC Repair Services in Rowlett, Texas
Getting Plumbing, Heating & AC repair services by professionals who have the tools and the know-how to be able to correctly diagnose and fix problems is very important in making sure your plumbing, heating and air conditioning problems don’t cause you any more trouble.
When your HVAC system or plumbing becomes damaged or stops working, it can be difficult to navigate what to do from there. HVAC and plumbing products you can find on the market are usually very cheap, but often only offer a temporary fix to the problem instead of a permanent one. This can cause even more damage and can end up costing you a lot more to fix your air conditioner or plumbing system.
That’s where we come in.
At Air Force One Plumbing, Heating & Air we have been providing professional, friendly services for over 25 years near Rowlett TX. We know how important it is for you to be able to use your HVAC and plumbing systems right when you need them, so we always make sure that we work quickly without compromising on the quality of our work.
Count on Air Force One for:
For more information on the services we offer in the Rowlett area, give us a call at 469-476-4846 today!
Why Choose Us:
- We treat our customers like family.
- 24/7 emergency HVAC services available.
- We get the job done right the first time.
- We have over 25 years’ experience.
for Rowlett, TX
Our Reviews by City
Bob - Rowlett, TX
Arrived on time and did an excellent job!
Kevin was great
John - Rowlett, TX
Kevin is conscientious and professional.
Fast, clean, good price
robert - Rowlett, TX
Great service. Very professional. Good price.
I know Kevin from servicing our office. He was very understanding and seemed honestly concerned. He was the same way when he serviced the office. I d
Brenda - Rowlett, TX
Thought the price of replacing the item was somewhat high. I dont.know what you all pay for it but I know a lot of factors are involved in pricing a item.
Great service and awesome price!
jb - Rowlett, TX
I am extremely happy with the service, price, and ethics. I was told by a competitor blower motors for my unit were no longer available and I needed a new unit for $2900. I called Air Force One for another opinion. They replaced the blower motor for less than $600. Thanks Air Force One!
Very prompt and professional
roberr - Rowlett, TX
Keven did an excellent
great follow-up to last month's check-up
Bill - Rowlett, TX
Makes me glad that I do business with them
Courteous, Efficient, and Knowledgeable
Ben - Rowlett, TX
They were able to get us a quick appointment, and the service tech diagnosed and fixed the problem quickly!
doug - Rowlett, TX
Excellent service, friendly and professional technician, but pricey
Bill - Rowlett, TX
great prompt service
Mark - Rowlett, TX
always a pleasure to deal with honest folks
Crew did a great job. Part of the same group that installed the unit.
Nick - Rowlett, TX
I was a little suprised that such a major Trane component failed in less than three years. Glad that parts where still under warranty.
Response from Air Force One Plumbing, Heating & Air:
Thanks for the review! We love to hear praise from our satisfied customers. I will tell the install crew that you gave them a thumbs up.
Technician arrived and found water heater pilot off. Technician attempted multiple times to relight pilot but piezo igniter would not spark and pilot cannot be lit. Due to age of system no OEM parts are available for repair and technician has created an estimate for water heater replacement.
Will reconvene with customer with warranty parts please see pictures attached
Technicians arrived and found fill valve in toilet constantly running. The angle stop connecting the supply line was not shutting completely so technicians opened water meter and shut off water at the street. The existing angle stop, supply line and fill valve were removed and replaced with new parts. The water was turned back on and angle stop, supply line, and fill valve were checked for leaks. No leaks were present and toilet was tested and found to be filling appropriately and shutting off when satisfied. During repairs the toilet bad was found to not be properly secured to the tile and bolts were found to be corroded. Customer was informed of the toilet not being properly secured and further repairs or toilet and flange replacement were recommended.
Upon arrival found bad cap for outside condenser unit replaced the system is working normally at this time recommended to the customer to have us come out and take a second more thorough look of the entire system and give him a itemized breakdown of what is going to break 1st on his system
Reistalled new drain pan and jones valve on both drain lines. Installed float switch on drain pan and blew out drain line.
Replaced indoor fan motor system is working properly at this time Inform the customer about the furnace being from 2005 Customer understands and knows that the potential for problems is high in the future
Inspected evaporator coils and condensate lines for any build up or growth nothing was found strange oder determined to not be a/c related
Gave the customer a quote for a new system customer will get back to us with their decision
Replaced indoor fan capacitor customers going to give us a call back in a month for a follow visit to check on the rest of the system help
Found bad contactor replace
Checked 1 system AC and heat. Checked heat just superficially. 39 degree split. Checked AC 20 degree split. Drain pan is rusted. Primary drain line is clogged. Blower motor and duct work are in good conditions. Checked condensing unit. Coil is plugged. Will need to be chemically cleaned. Compressor and fan motor amps are working range. Capacitor and contactor are good. Sent quote for all repairs.
Found Knick on the refrigerant line. Too close to roofline and insulation, donâ€™t want to risk burning house down. Will have to run new lines. Scheduled for Friday 7/16/21 at between 3-5 PM.
Fan and compressor motors are both out. Tried to see if capacitor and hard start kit would help and it did not. Will need to replace system as it is r-22. Sent estimate and will have customer sign up for financing. Once approved we will schedule for the next available time.
System was low on r-410A. Added a pound and a half in to the system. Added leak stop with UV dye. Will come back in the future to assess where leak is and see if it is repairable. 21 degree temperature differential. No other issues found at this time. Filter: 20X25X1
Quotes for 16 and 17 SEER 3 ton full systems + 12 ducts
Drain line was clogged and replaced an elbow. Unclogged drain line. No other issues found at this time. Customer signed up for membership.
One time maintenance on 40 year old system. Electrical components are working properly. 2 1/2 pounds low on r-22. Added refrigerant and tested system. It is cooling 18 degree split at this time. Gave customer an informal quote for a new system replacement they will decide in the winter.
Replaced fan motor
Full system estimate. Gave 14 SEER and 20 SEER estimates to customer. Will call back when they decide which route they want to go. 20 SEER systems are 4-6 weeks delayed. Gas horizontal 80% furnace 4 ton condenser and evaporator coil.
Customer had two inline bathrooms that were clogged. Technicians found clean out and attempted to use camera to identify clog but due to the angle of the pipes camera was not able to move towards the house. Technicians then removed toilet in the bathroom and attempted to use camera to identify blockage. After several attempts blockage was not able to be clearly identified on camera and therefore augering was not attempted or recommended. Technicians referred customer to Berkeys for further evaluation.
1 system spring PM. Checked electrical components. Replaced air filter. Checked temperature differential. Cleaned coil. Checked refrigerant pressures. No issues found at this time. System is ready for summer weather. Customer renewed membership.