Exceptional Plumbing, Heating & Cooling Services in Rowlett, Texas
When your HVAC or plumbing becomes damaged or stops working, it can be difficult to navigate what to do from there. HVAC and plumbing products you can find on the market are usually very cheap, but often only offer a temporary fix to the problem instead of a permanent one. This can cause even more damage and can end up costing you a lot more to fix.
Getting repair services by professionals who have the tools and the know-how to be able to correctly diagnose and fix problems is very important in making sure your plumbing, heating and air conditioning problems don’t cause you any more trouble. That’s where we come in.
At Air Force One Plumbing, Heating & Air we have been providing professional, friendly services for over 25 years. We know how important it is for you to be able to use your HVAC and plumbing systems right when you need them, so we always make sure that we work quickly without compromising on the quality of our work.
Count on Air Force One for:
For more information on the services we offer in the Rowlett area, give us a call at 469-476-4846 today!
Why Choose Us:
- We treat our customers like family.
- 24/7 emergency HVAC services available.
- We get the job done right the first time.
- We have over 25 years’ experience.
for Rowlett, TX
Our Reviews by City
Bob - Rowlett, TX
Arrived on time and did an excellent job!
Kevin was great
John - Rowlett, TX
Kevin is conscientious and professional.
Fast, clean, good price
robert - Rowlett, TX
Great service. Very professional. Good price.
I know Kevin from servicing our office. He was very understanding and seemed honestly concerned. He was the same way when he serviced the office. I d
Brenda - Rowlett, TX
Thought the price of replacing the item was somewhat high. I dont.know what you all pay for it but I know a lot of factors are involved in pricing a item.
Great service and awesome price!
jb - Rowlett, TX
I am extremely happy with the service, price, and ethics. I was told by a competitor blower motors for my unit were no longer available and I needed a new unit for $2900. I called Air Force One for another opinion. They replaced the blower motor for less than $600. Thanks Air Force One!
Very prompt and professional
roberr - Rowlett, TX
Keven did an excellent
great follow-up to last month's check-up
Bill - Rowlett, TX
Makes me glad that I do business with them
Courteous, Efficient, and Knowledgeable
Ben - Rowlett, TX
They were able to get us a quick appointment, and the service tech diagnosed and fixed the problem quickly!
doug - Rowlett, TX
Excellent service, friendly and professional technician, but pricey
Bill - Rowlett, TX
great prompt service
Mark - Rowlett, TX
always a pleasure to deal with honest folks
Crew did a great job. Part of the same group that installed the unit.
Nick - Rowlett, TX
I was a little suprised that such a major Trane component failed in less than three years. Glad that parts where still under warranty.
Response from Air Force One Plumbing, Heating & Air:
Thanks for the review! We love to hear praise from our satisfied customers. I will tell the install crew that you gave them a thumbs up.
Inspected evaporator coils and condensate lines for any build up or growth nothing was found strange oder determined to not be a/c related
Gave the customer a quote for a new system customer will get back to us with their decision
Replaced indoor fan capacitor customers going to give us a call back in a month for a follow visit to check on the rest of the system help
Found bad contactor replace
Checked 1 system AC and heat. Checked heat just superficially. 39 degree split. Checked AC 20 degree split. Drain pan is rusted. Primary drain line is clogged. Blower motor and duct work are in good conditions. Checked condensing unit. Coil is plugged. Will need to be chemically cleaned. Compressor and fan motor amps are working range. Capacitor and contactor are good. Sent quote for all repairs.
Found Knick on the refrigerant line. Too close to roofline and insulation, donâ€™t want to risk burning house down. Will have to run new lines. Scheduled for Friday 7/16/21 at between 3-5 PM.
Fan and compressor motors are both out. Tried to see if capacitor and hard start kit would help and it did not. Will need to replace system as it is r-22. Sent estimate and will have customer sign up for financing. Once approved we will schedule for the next available time.
System was low on r-410A. Added a pound and a half in to the system. Added leak stop with UV dye. Will come back in the future to assess where leak is and see if it is repairable. 21 degree temperature differential. No other issues found at this time. Filter: 20X25X1
Quotes for 16 and 17 SEER 3 ton full systems + 12 ducts
Drain line was clogged and replaced an elbow. Unclogged drain line. No other issues found at this time. Customer signed up for membership.
One time maintenance on 40 year old system. Electrical components are working properly. 2 1/2 pounds low on r-22. Added refrigerant and tested system. It is cooling 18 degree split at this time. Gave customer an informal quote for a new system replacement they will decide in the winter.
Replaced fan motor
Full system estimate. Gave 14 SEER and 20 SEER estimates to customer. Will call back when they decide which route they want to go. 20 SEER systems are 4-6 weeks delayed. Gas horizontal 80% furnace 4 ton condenser and evaporator coil.
Customer had two inline bathrooms that were clogged. Technicians found clean out and attempted to use camera to identify clog but due to the angle of the pipes camera was not able to move towards the house. Technicians then removed toilet in the bathroom and attempted to use camera to identify blockage. After several attempts blockage was not able to be clearly identified on camera and therefore augering was not attempted or recommended. Technicians referred customer to Berkeys for further evaluation.
1 system spring PM. Checked electrical components. Replaced air filter. Checked temperature differential. Cleaned coil. Checked refrigerant pressures. No issues found at this time. System is ready for summer weather. Customer renewed membership.
customer will go back to us if they're decision
Removed existing frost free outside hose bib which was leaking and replace with new frost free outside hose bib. New faucet was tested and no leaks present.
2 system spring PM. Checked blower motor amps. Checked temperature differentials. Inspected duct work and drain lines. Filters are clean left new ones with customer. Checked condensing units. Coils are clean. Checked electrical components. No issues found at this time. System is working as designed.
Customer installed new thermostat recently. Incorrectly wired O/B and it was on heat the entire time. Fixed issue and it is now cooling properly. No other issues found at this time. System is working as designed. Customer signed up for 1 year membership.
Clean the outside condenser coil check the system as a whole the compressor is showing signs of failure will reconvene with customer at later date to find out their decision for replacement told the customer about the future for the unit
1 system spring PM. Checked electrical components and temperature differential. Coil is clean. Will have to return and drop new filter off. No issues found at this time. System is ready for summer weather.
Perform system maintenance no recommendations at this time other than UV light to Help keep filters cleaner for longer
2 system spring PM. Checked blower motor amps. Checked temperature differentials. Inspected drain lines and duct work. Replaced air filters. Checked condensing units. Coils are clean. Checked electrical components. No issues found at this time. System is ready for summer weather.
Unit was low on refrigerant. Added 4 pounds of r-410a and added leak sealant with UV dye. Customer will call back if it stops cooling. Unit is cooling properly at this time.
Ensure that system is working to manufacturer specifications talk to customer about recommended repairs see invoice