Exceptional Plumbing, Heating & Cooling Services in Rowlett, Texas
When your HVAC or plumbing becomes damaged or stops working, it can be difficult to navigate what to do from there. HVAC and plumbing products you can find on the market are usually very cheap, but often only offer a temporary fix to the problem instead of a permanent one. This can cause even more damage and can end up costing you a lot more to fix.
Getting repair services by professionals who have the tools and the know-how to be able to correctly diagnose and fix problems is very important in making sure your plumbing, heating and air conditioning problems don’t cause you any more trouble. That’s where we come in.
At Air Force One Plumbing, Heating & Air we have been providing professional, friendly services for over 25 years. We know how important it is for you to be able to use your HVAC and plumbing systems right when you need them, so we always make sure that we work quickly without compromising on the quality of our work.
Count on Air Force One for:
For more information on the services we offer in the Rowlett area, give us a call at 469-476-4846 today!
Why Choose Us:
- We treat our customers like family.
- 24/7 emergency HVAC services available.
- We get the job done right the first time.
- We have over 25 years’ experience.
for Rowlett, TX
Our Reviews by City
Bob - Rowlett, TX
Arrived on time and did an excellent job!
Kevin was great
John - Rowlett, TX
Kevin is conscientious and professional.
Fast, clean, good price
robert - Rowlett, TX
Great service. Very professional. Good price.
I know Kevin from servicing our office. He was very understanding and seemed honestly concerned. He was the same way when he serviced the office. I d
Brenda - Rowlett, TX
Thought the price of replacing the item was somewhat high. I dont.know what you all pay for it but I know a lot of factors are involved in pricing a item.
Great service and awesome price!
jb - Rowlett, TX
I am extremely happy with the service, price, and ethics. I was told by a competitor blower motors for my unit were no longer available and I needed a new unit for $2900. I called Air Force One for another opinion. They replaced the blower motor for less than $600. Thanks Air Force One!
Very prompt and professional
roberr - Rowlett, TX
Keven did an excellent
great follow-up to last month's check-up
Bill - Rowlett, TX
Makes me glad that I do business with them
Courteous, Efficient, and Knowledgeable
Ben - Rowlett, TX
They were able to get us a quick appointment, and the service tech diagnosed and fixed the problem quickly!
doug - Rowlett, TX
Excellent service, friendly and professional technician, but pricey
Bill - Rowlett, TX
great prompt service
Mark - Rowlett, TX
always a pleasure to deal with honest folks
Crew did a great job. Part of the same group that installed the unit.
Nick - Rowlett, TX
I was a little suprised that such a major Trane component failed in less than three years. Glad that parts where still under warranty.
Response from Air Force One Air Conditioning:
Thanks for the review! We love to hear praise from our satisfied customers. I will tell the install crew that you gave them a thumbs up.
Replaced old thermostat with a new Honeywell pro 3000 more efficient better accuracy of temperature
ONE SYSTEM PREPAID HEAT CHECK. TD-51 OK. FILTER WAS OK. LEFT NEW 20X25X1. Co INSIDE AIRSTREAM 0 PPM OK. Co GOING OUT FLUE PIPE 44 PPM OK. CLEANED OFF FLAME SENSOR. MOTOR AMPS OK. BLOWER WHEEL OK. ALL SAFETIES TEST OK. HEAT CHECKS OUT . WORKING FINE ON TEST DATE.
ONE SYSTEM PREPAID HEAT CHECK. TD-51 OK. Replaced 20x25x4 filter . Co INSIDE AIRSTREAM 0 PPM OK. Co GOING OUT FLUE PIPE 18 PPM OK. CLEANED OFF FLAME SENSOR. MOTOR AMPS OK. BLOWER WHEEL OK. ALL SAFETIES TEST OK. HEAT CHECKS OUT . WORKING FINE ON TEST DATE.
Diagnosis unit number 4 found to defective expansion browns causing damage to the outside compressor system outside needed to be turned off or calling anymore damage or exploding the compressor terminal will need to replace 2 expansion valves & compressor w/ liquid line dryers, including 9 to 18 pounds of refrigerant
Prepaid maintenance check up rheem system furnace inspection no problems detected all working properly.
Defective pressure switch causing heater to never come on and eventually looking out on diagnostic code 3 which states pressure switch not closing recommend replacing defective pressure switch customer declined said he could replace himself if you have any questions or help needed to replace it don't hesitate to call thank you for your business you are technician Ricardo from Air Force One ac
TWO SYSTEM HEAT CHECK. T.D. 50,55 - OK. REPLACED ALL FILTERS 20X24x1-2, CO GOING OUT FLUE PIPE 10-42/PPM. CO INSIDE AIRSTREAM 0/PPM - OK. CLEANED FLAME SENSORS (2). CAPACITORS - OK. MOTOR AMPS OK. BLOWER WHEELS OK. TESTED PRESSURE SWITCHES & SAFETYS - TESTED OK. HEAT CHECKS OUT WORKING FINE ON TEST DATE
Replaced 1/4hp 460v condenser fan motor on unit 4, carrier condenser
Installed 2.5 ton rheem condenser
Found leak in downstairs rheem evaporator coils, will need to be replaced
Air sealed all supply ducts on a allstyle plenum coil
Replaced 2 pole sequencer on a rhemm air handler, sequencer was stuck causing heat to be on with cooling
Found lennox compressor shorted to ground, needs to replace compressor or entire system
Replaced ruud variable speed dB blower module.
Replaced swollen capacitor on York condenserall working fine
Replaced 55-5 capacitor on a trane condenser. Will return to perform complete cooling tune up.
Blew out main drain line with compressed air.
Preventive maintenance check up one system rheem replace filters wash outside condenser coils check motor amps refrigerant levels normal system working fine
Technician Ricardo performed to prepaid cooling checks the back dream kitchen system could not find any reason why it was not cooling Systems charge is normal and is doing a 20 degree temperature difference the front system found no issues other than the screws on the top are a bit too loose causing water to drip in and around them need to enlarge all the screws from five sixteenths other than that not sure what's going on in the kitchen
Cooling Check of one lennox system. Filter was ok, washed condenser coils, replaced fan motor capacitor, recommended ceiling saver,checked motors, capacitors and electrical.
Cooling Check of one york system. Changed filter, washed coils, checked motors, capacitors and electrical.
Cooling Check of 3 ebb systems. Replaced 3 capacitors and a start kit. Replaced 2 rheem control boards for the condenser
Checked r 22 charge, normal, coil had defrosted, system operating as intended
Cooling check of one rheem system. Replaced filter 20x25x4, washed condenser coils, checked motors, capacitors and electrical. Checked 410a charge.
Evaporator coil frozen, rescheduled to check system