Exceptional Plumbing, Heating & Cooling Services in Rowlett, Texas
When your HVAC or plumbing becomes damaged or stops working, it can be difficult to navigate what to do from there. HVAC and plumbing products you can find on the market are usually very cheap, but often only offer a temporary fix to the problem instead of a permanent one. This can cause even more damage and can end up costing you a lot more to fix.
Getting repair services by professionals who have the tools and the know-how to be able to correctly diagnose and fix problems is very important in making sure your plumbing, heating and air conditioning problems don’t cause you any more trouble. That’s where we come in.
At Air Force One Plumbing, Heating & Air we have been providing professional, friendly services for over 25 years. We know how important it is for you to be able to use your HVAC and plumbing systems right when you need them, so we always make sure that we work quickly without compromising on the quality of our work.
Count on Air Force One for:
For more information on the services we offer in the Rowlett area, give us a call at 469-476-4846 today!
Why Choose Us:
- We treat our customers like family.
- 24/7 emergency HVAC services available.
- We get the job done right the first time.
- We have over 25 years’ experience.
for Rowlett, TX
Our Reviews by City
Bob - Rowlett, TX
Arrived on time and did an excellent job!
Kevin was great
John - Rowlett, TX
Kevin is conscientious and professional.
Fast, clean, good price
robert - Rowlett, TX
Great service. Very professional. Good price.
I know Kevin from servicing our office. He was very understanding and seemed honestly concerned. He was the same way when he serviced the office. I d
Brenda - Rowlett, TX
Thought the price of replacing the item was somewhat high. I dont.know what you all pay for it but I know a lot of factors are involved in pricing a item.
Great service and awesome price!
jb - Rowlett, TX
I am extremely happy with the service, price, and ethics. I was told by a competitor blower motors for my unit were no longer available and I needed a new unit for $2900. I called Air Force One for another opinion. They replaced the blower motor for less than $600. Thanks Air Force One!
Very prompt and professional
roberr - Rowlett, TX
Keven did an excellent
great follow-up to last month's check-up
Bill - Rowlett, TX
Makes me glad that I do business with them
Courteous, Efficient, and Knowledgeable
Ben - Rowlett, TX
They were able to get us a quick appointment, and the service tech diagnosed and fixed the problem quickly!
doug - Rowlett, TX
Excellent service, friendly and professional technician, but pricey
Bill - Rowlett, TX
great prompt service
Mark - Rowlett, TX
always a pleasure to deal with honest folks
Crew did a great job. Part of the same group that installed the unit.
Nick - Rowlett, TX
I was a little suprised that such a major Trane component failed in less than three years. Glad that parts where still under warranty.
Response from Air Force One Plumbing, Heating & Air:
Thanks for the review! We love to hear praise from our satisfied customers. I will tell the install crew that you gave them a thumbs up.
1 system spring PM. Checked electrical components and temperature differential. Coil is clean. Will have to return and drop new filter off. No issues found at this time. System is ready for summer weather.
Perform system maintenance no recommendations at this time other than UV light to Help keep filters cleaner for longer
2 system spring PM. Checked blower motor amps. Checked temperature differentials. Inspected drain lines and duct work. Replaced air filters. Checked condensing units. Coils are clean. Checked electrical components. No issues found at this time. System is ready for summer weather.
Unit was low on refrigerant. Added 4 pounds of r-410a and added leak sealant with UV dye. Customer will call back if it stops cooling. Unit is cooling properly at this time.
Ensure that system is working to manufacturer specifications talk to customer about recommended repairs see invoice
Will provide customer with quote for new tank and tankless water heater.
Replace draft motor
Diagnosed bad motherboard blower motor and transformer talk to customer customer is going to find parts cheaper elsewhere and if not give us a phone call back
Inspected outside clean out for leaks. Found no leak. Ran water in upstairs fixtures. Replicated problem in upstairs front faucet. Unable to locate source of leak with camera. Referred customer to Berkeys
Inspected washroom sink, small leak from stops. Recommended replacing them on a later date. Customer reported washer lines not working. Inspected the lines and are now working. Small leak found on the hot water washerbox valve recommended replacement.
Replaced blower wheel. Ran tested unit and it is heating properly now. No other issues found at this time.
System was not cycling through heat. Inducer motor has a bad connection on one of the prongs. Will have to replace motor tomorrow. Was able to rig it to work for now. Customer will probably sign up for member tomorrow. Will take off difference of $139 diagnostic if they do.
Blower wheel became loose. Will replace wheel on Monday or Tuesday when part is in. System is working for now but is very loud.
Installed heat kit. 38 degree temperature differential. System is working as designed at this time. No other issues found.
No heat right side of house. Pressure switch stuck open code on board. Cleaned inducer port. Tested system and it came on. System is working properly at this time now. No other issues found.
Replace rough in inside wall by cutting portion of wall away to expose internal piping. Replace outer trim with customer supplied single valve trim kit. Difficult access.
Replace rough in inside wall by cutting portion of wall away to expose internal piping. Replace outer trim with customer supplied single valve trim kit. Normal access.
Plumbing estimate for two water shut off valves, 1 customer supplied sink, and 1 customer supplied shower trim kit
Ac not blowing air
Replaced old thermostat with a new Honeywell pro 3000 more efficient better accuracy of temperature
ONE SYSTEM PREPAID HEAT CHECK. TD-51 OK. FILTER WAS OK. LEFT NEW 20X25X1. Co INSIDE AIRSTREAM 0 PPM OK. Co GOING OUT FLUE PIPE 44 PPM OK. CLEANED OFF FLAME SENSOR. MOTOR AMPS OK. BLOWER WHEEL OK. ALL SAFETIES TEST OK. HEAT CHECKS OUT . WORKING FINE ON TEST DATE.
ONE SYSTEM PREPAID HEAT CHECK. TD-51 OK. Replaced 20x25x4 filter . Co INSIDE AIRSTREAM 0 PPM OK. Co GOING OUT FLUE PIPE 18 PPM OK. CLEANED OFF FLAME SENSOR. MOTOR AMPS OK. BLOWER WHEEL OK. ALL SAFETIES TEST OK. HEAT CHECKS OUT . WORKING FINE ON TEST DATE.
Diagnosis unit number 4 found to defective expansion browns causing damage to the outside compressor system outside needed to be turned off or calling anymore damage or exploding the compressor terminal will need to replace 2 expansion valves & compressor w/ liquid line dryers, including 9 to 18 pounds of refrigerant
Prepaid maintenance check up rheem system furnace inspection no problems detected all working properly.
Defective pressure switch causing heater to never come on and eventually looking out on diagnostic code 3 which states pressure switch not closing recommend replacing defective pressure switch customer declined said he could replace himself if you have any questions or help needed to replace it don't hesitate to call thank you for your business you are technician Ricardo from Air Force One ac