Get your comfort on in The Colony, TX with top quality services from the plumbing, heating and cooling professionals at Air Force One. We have over 25 years of industry experience.
We are a family company dedicated to providing you with family treatment. Read recent reviews of our five star plumbers and HVAC techs from your own The Colony, TX community.
for The Colony, TX
Our Reviews by City
Fixed a freezing coil
Andrew - The Colony, TX
Timely, quick, got right to the heart of the problem, explained my options fully, and had the unit up and running all within an hour.
Maintenance check 2 systems furnace inspection, filters were ok, pressure switch ports clear, cleaned flame sensors 2 inducer motor amps :ok Blower wheels ok, Co going out flue pipes 34-50ppm,Co inside airstream 0ppm ok both working properly
Defected evaporator coil added 4pounds system under warranty will replace system recharged until new coil comes in
Technician Ricardo worked on an upflow r22 r22 refrigerant system.... condenser located on rooftop.. hatch located near the outside stairs w/ attic stairs & found leak at suction line shut off valve cap added leaklock to the threads added 1lbs r22 everything inside looked brandnew...lol....but otherwise system cooling back to normal....ready 4 summer
Cooling check on a down flow r22 unit ....water washed condenser ....cleaned out all the ants in her electronics.... changed the 20 X 25 X 4 filter ...the blower and coils were clean ...drains were cleared and summer treated with bleach tablets ....has a variable speed blower and the temperature drop across the equipment was 20 degrees.... no issues were found other than the ants ....system is ready for summer
Technician Ricardo and Dale replaced indoor plenum evaporator coil and refrigerant dryers due to coil leaking refrigerant air shield all connections pressure tested refrigerant lines recharged system tested cooling
Maintenance check up on 2 rheem systems 14.5 seer,both in excellent working conditions
Heating Check 2 systems